Chemical plant tank area propylene oxide gas detection alarm
Detailed summary: Installation instructions of propylene oxide gas detection alarm probe (detector) in chemical plant tank area:Product Type: Location: Jinan Updated: 2020-01-11 Leave message
1. The combustible gas detector wiring should adopt three-core shielded cable, with a single wire diameter greater than 1 square millimeter, and the shielding layer must be grounded when wiring.
2. The on-site wiring of the flammable gas detector should pass through the pipe, the pipe used should meet the fire protection requirements, and the pipe should be connected with the probe to meet the fire protection requirements.
Chemical plant tank area acrylic gas concentration display alarm
Detailed summary: Common faults of acrylic gas concentration display alarm in tank area of chemical plant are: low fault and high fault. The fault is a line problem or the detector is broken. The host is in a no-load state and therefore reports a low fault. A high fault is caused by a defective sensor, a wrong connection of the detector, or a defective detector main board.Product Type: Location: Jinan Updated: 2020-01-11 Leave message